Aboveground fuel oil storage tanks
Department of Civil and Environmental Engineering
Master of Science
Peck, Charles Franklin
Stack, William J.
A review of the American Petroleum Institute Standard 650 and Appendixes points out the advantages of using high strength steel and the variable point design method (Appendix K) to obtain reasonably uniform shell stresses. Design limitations imposed by notch toughness and residual stresses are pointed out.
Design considerations for the installation of an internal floating roof in a standard cone roof tank are discussed. Methods of calculating evaporation losses and an economic justification for a floating roof are included. Budget estimate figures have been compiled as a function of tank capacity for tanks, site preparation and tank ringwall or piled mat foundations.
Installation of a storage tank is subject to government approval by the State of New Jersey Department of Labor and Industry and Environmental Protection. A review of title 12:133 of the New Jersey Administrative Code (NJAC) "Flammable and Combustible Liquids" as it applies to tank construction was made. The requirements of the Occupational Safety and Health Act (OSHA) follow (NJAC) specifications.
njit-etd1973-003 (79 pages ~ 2,883 KB pdf)
Please complete this Feedback Form to inform us about your experience using this website. It will assist us in better serving your information needs in the future. Thank You!
Created April 13, 2006